ection of iron pipe for these pressures was, first, as between steel and cast-iron; and, second, as between the lead joint of the standard bell and spigot pipe and the machined iron joint of the universal joint pipe. Again, the choice was as between lead and leadite for the bell and spigot pipe.
Cast iron was selected because of the certainty of its long life, and the bell and spigot pipe was selected on the basis of comparative costs for pipe laid. The standard lead joint was chosen on the result of tests. This cast-iron pumping main has a diameter of 12 in. throughout.
_Pipe Weights._--Makers of standard bell and spigot pipe urged the usual heavy weights selected for municipal service and heavy water-hammer. Three pressures, viz., 217, 260, and 304 lb., were used for the division of pipe weights, on which the standard pipe-makers specified shell thicknesses of 0.82, 0.89, and 0.97 in. Eliminating water-hammer and adopting a working stress of 2,400 lb., the thicknesses are reduced to 0.54, 0.6
VOLUME ONE in the WOOD COW CHRONICLES series. <... Read more
2013 SFR GALAXY AWARD WINNER
"Heroism and... Read more
Fans of paranormal and urban fantasy will enjoy... Read more
There are six secret clans across the world–Afr... Read more
Set in the late Georgian era, Elizabeth Bailey’... Read more
"Tim Hurtletuta has forgotten something. He can... Read more
12th century England: Two men vie for the thron... Read more
Dr. Gabe Allen has a rule about dating colleagues... Read more
See more popular titles from this genre.